Welcome to Acme Electric’s frequently asked questions page.
I am sure you have a few questions on how to get started, so lets get you started…there are multiple ways to browse this site:
- Search Box: This is going to be the quickest way to locate exactly what you are looking for, type a few key words and select the FAQ that best matches your inquiry.
- Recent Posts: This the most recent questions to be answered.
- Categories: This will allow you to browse based on a general subject, and see all of the FAQ’s relevant to that topic.
If those three fail, shoot us your question and we will work to get it answered and added to our growing knowledge database.
Have a question about a specific product, or want to place an order with Acme, there are various ways to contact us!
No. The I-Trap™ is specifically designed to reduce high neutral currents.
First, increasing the neutral size does not eliminate the harmonic problem – they are still present in the system and may cause transformer overheating and possibly failure.
Second, installation of a new neutral conductor in long runs may be difficult and cost prohibitive when compared to the cost of installing an I-Trap™ unit.
Harmonic filters must be matched to their load and they may cause a leading power factor, which, when tuned to a specific frequency, can actually aggravate the harmonic problem.
The I-Trap™ will not increase three phase or phase-to-phase fault currents but can increase the available fault current on line to ground faults.
Phase amps have been reduced by 18% in Acme laboratory tests. Depending on the conditions for a particular electrical system, the percentage will vary.
Yes. Lab tests have shown significant reductions.
It is for use on 208Y/120V systems only. For other voltages, contact the factory.